Großartig Honeywell Boiler Aquastat Schaltplan Zeitgenössisch - Most wood boilers have an aquastat that turns the pump on while the boiler water is up to temp. In case you need to control the pump with a thermostat you use a pump relay like a taco sr501 to control the pump. The thermostat calls in the relay which activates the pump or you use a line voltage thermostat in preference to a low voltage thermostat and a relay. If you cord an aquastat in series with the relay pump circuit the pump will most effective run while the water is up to temp. Every other technique is to neglect the second one stat and simply have the pump run off an aquastat. This will give you some gravity air movement while there may be no call for heat from the thermostat but since the wood boiler is burning all the time this normally has little impact on basic room comfort. Ok, this manipulate is not suitable to your software. It's made for an air handler now not a furnace. I'm able to put up a greater not unusual answer in an effort to paintings as long as you have got g cord linked to the thermostat.
There should be a g terminal at the furnace terminal strip in which the thermostat is hooked up. With this technique you handiest want one thermostat. You may use a 2d thermostat to govern the wood boiler if you like. Here are the commands:. Welcome to just answer, my name is ***** ***** i will do my quality that will help you with your trouble. First i’ll need some greater data so i've a extra whole photo of you state of affairs.
The way that is generally performed is to apply a strap on aquastat connected to the new water go back line from the boiler coil within the furnace plenum. You need an aquastat with nc (commonly closed) and no (normally open) terminals like a honeywell l6006c1018. You disconnect the lead that's attached to w on the furnace terminal strip (typically white from the thermostat) then join it to the commonplace terminal on the aquastat. Then join the aquastat terminal that makes (closes the transfer to not unusual) on temp rise to g on the furnace terminal strip and the nc terminal to w on the furnace terminal strip. With it stressed out this manner whilst the water in the coil is not hot the furnace burner is referred to as in through making r to w and handiest the blower runs through making r to g whilst the water inside the coil is warm .